MLSS is used to measure the TSS in activated sludge, while MLVSS is used to measure the concentration of biomass in activated sludge.
SBR0 followers0 questions0 posts
Interested in this Topic?
Signup up or log in now to follow this topic, join the discussion, and always stay updated.
Return activated sludge, or RAS, is used to maintain the population of microorganisms needed for reaction to proceed in the aeration tank. In a way, this is a method of optimization in wastewater treatment.
Take a sample of the supernatant liquid and have it analyzed for TSS. If the TSS is high, adjust your MLSS so that it is according to the design. This could be due to short circuiting of the chlorine contact... (More)
Several factors could cause foaming in the SBR and the CCC, sometimes even in the equalization tank.
1. First, check that you are not overaerating; the maximum DO in each tank should be at 4mg/L. If it's more than that,... (More)